A. Prepare the hose and air pump (recommended brand: OUTSTANDING Aotus, model 2200W-40L; selection basis: the internal volume of the system is about 1.5m3 / h, according to the time required to choose the corresponding exhaust volume air pump; the highest output air pressure required 8bar or more, 10bar best).
B. According to the "AntSpace field installation manual" connected to the external pipeline.
C. Check whether the plug or ball valve on the automatic exhaust valve on the internal pipeline of the container and the external connection pipeline are all closed (screw the top nut of the automatic exhaust valve to open/close the automatic exhaust valve) (see Figure 1 to Figure 4).
D. Start system pressurization.
Figure 1 Pump station - automatic venting valve
Figure 2 Automatic exhaust valve opening and closing diagram
Figure 3 External connection line - automatic exhaust valve
Figure 4 Diagram of ball valve opening and closing
*Note: This is the water-cooled container parameters of CNA version 1.3, if your product is other manufacturers or other versions, may be slightly different from this parameter, this parameter is for reference only.
If you have any questions, please feel free to contact BITMAIN Customer Support.