The system is divided into internal circulation and external circulation, where the internal circulation medium is coolant and the external circulation medium is tap water; the system is set up with filters to filter the internal and external circulation, and the filters need to be cleaned when the system runs for a period of time.
The filter is divided into three places, and its corresponding cleaning time requirements are as follows:
- Cooling tower spray pump suction port filter, the cleaning cycle is once a month.
- Pump group liquid supply system internal circulation Y filter, the cleaning cycle is once a year.
- Pump group replenishment system internal circulation Y filter, cleaning cycle for once a year.
The cleaning method is: wash by water and rinse clean and dry before use.
*Note: This is the water-cooled container parameters of AVIC version 1.3, if your product is other manufacturers or other versions, may be slightly different from this parameter, this parameter is for reference only.
If you have any questions, please feel free to contact BITMAIN Customer Support.
Please sign in to leave a comment.