The container water cooling system should be turned off the main power supply when it is not used for a long time.
--This will prevent accidents from happening.
Allow only qualified and authorized personnel to perform maintenance and other operations on electrical systems.
(1) The cooling system in the container should be equipped with a fire extinguisher before starting; (equipment to increase the fixed location of the fire extinguisher, or have the relevant installation instructions)
(2) equipment must be reliably grounded, should verify the protective grounding resistance to ensure continuity, which should be less than 0.3Ω, otherwise there may be dangerous situations that lead to personal injury or death.
(3) only after shutdown and turn off the power to clean the equipment, otherwise it may be electrocuted or injured, do not use water to clean the equipment, otherwise it may be electrocuted.
(4) Always check whether the valve (if there is a valve) is open before starting the machine.
(5) Electrical distribution cabinet and electric control box operation safety provisions.
Before the operation of the distribution cabinet A/B and electric control box, should ensure that the cabinet door is in a locked state to prevent personal injury such as electric shock, while avoiding salt spray, moisture, dust in the air or other conductive substances into the interior of the distribution cabinet and electric control box.
When the power is on, it is forbidden to touch the single board, cables, terminals, modules, sensors and other equipment inside the cabinet to avoid causing safety accidents.
(b) In case of malfunction, odor or abnormal sound, turn off the main circuit breakers MCB-A1, MCB-A2 and MCB17 of the three electric cabinets or press the emergency stop button on the container door as well as the two electric cabinets, otherwise it may lead to electric shock or fire accidents.
Translated with www.DeepL.com/Translator (free version)
(1) It is prohibited to open the switchboard door by non-professional authorized personnel.
(2) The switchboard door can be opened only when the main circuit breaker is in the OFF position.
Please read this manual carefully before using this equipment, if you have any difficulties or problems, please ask for help from the factory.
*Note: This to the Air China version 1.3 water-cooled container parameters, if your product for other manufacturers or other versions, may be slightly different from this parameter, this parameter is for reference only.
If you have any questions, please feel free to contact the Ant Mining Machine after-sales service
|Contact us >|