AntSpace HK3 V2 Container System Power-on and Power-off Process
1.The switches in the electric control cabinet are shown in the figure below:
Figure 1 Internal view of electric control cabinet
2. Precautions when the system is powered on for the first time
After the entire system is connected, the unit can be powered on for debugging.
However, before powering on, it is also necessary to use a multimeter to measure whether there is a short circuit between the phases of the two power supplies, between phases and zero, between phases and ground, and between zero and ground. If not, it means it can be powered on normally. If there is a short circuit to any of the above, you should troubleshoot the problem before powering up.
After the front end of the system is powered on (the system itself is not yet powered on), it is necessary to measure the voltage of the front end to see if it meets the power requirements of the device.
The power requirements of the device are: AC415V±5%, 60Hz
3. System power-up sequence
When the front end of the system is powered on and the voltage meets the requirements of the device, the system can be powered on at this time.
a: First power on the electric control cabinet:
When the electric control cabinet door is opened, first open MCB17, then open MCB 18, MSS6, and then open the front circuit breaker of the inverter. MCB-DC1, MCB-DC2 and MCB-DC3 are 24V, 12V and 5V DC switches. After powering up, make sure the three switches are on. At this point, the screen and PLC on the cabinet door start to work.
When the electric control cabinet door is closed and the system needs to be powered on, first turn on the protection switches of MCB18, MSS6, MCB-DC1, MCB-DC2, MCB-DC3 and the front end of the inverter in the cabinet, then close the cabinet door, and open it through the cabinet door operating handle MCB17. At this point, the unit is powered up.
A trained electrician can operate the system through the touch screen, set parameters, modify thresholds, change operating modes (auto/manual), start and stop a motor individually or run automatically. At this time, the liquid cooling system can be operated first, and the temperature of the liquid supply can be controlled within the required temperature range, and then the conditions for opening the computing unit can be met.
b: After the electric control cabinet is powered on, according to the operation process of the control system, when the temperature of the supply liquid is maintained near the target temperature, the conditions for starting the computing unit are met. At this point, you can open the circuit breakers in power distribution cabinets A and B to start powering on the computing unit. The power-on sequence of the PDC is as follows:
First open MCB-A1, A2, then open MCB-15, 16, 21, 22, B1, B2, and then start the rows of computing units in an orderly manner as required. Since there are 210 computing units in total, there are 14 rows in total. When starting the computing unit, after starting one row (15 computing units), the next row should be started at an interval of 20S, and so on.
4. System power down sequence
When the system is powered off for some reason, the power supply of the computing unit is first disconnected according to the requirements. This is to ensure that the water temperature before and after the power failure of the computing unit is the same, which is equivalent to protecting the power module of the computing unit.
When the computing unit is powered off, and the liquid cooling system is manually stopped through the touch screen, the water temperature will rise slightly at this time, but it has no effect on the system. Finally, disconnect the main power supply of the electric control box and the power distribution cabinet, so that the whole system is in a state of complete power failure.
The above practice is the behavior of safe power off. However, when there is a serious fault in the system, you can directly press the emergency stop button on the inner door of the container to make the main circuit breaker of the power distribution cabinet and the main circuit breaker of the electric control box trip instantaneously, so that the system is completely powered off. It is convenient for professionals to carry out maintenance work.
*Note: This parameter is based on AVIC 1.3 version of the water-cooled container. If your product is from other manufacturers or other versions, it may be slightly different from this parameter. This parameter is for reference only.
Should you have any inquiries, feel free to contact us for assistance.
|Contact us >|
Please sign in to leave a comment.