|No. of Floors||2|
|Single-story factory area||8000 m2|
|Number of transformers||40|
|Single factory power capacity||126 MW|
|Single load reference cost||420,000RMB/MW|
|Single machine reference cost||550-700 RMB|
1. Rack standardized design (standardization of external dimensions, standardization of structural combination)
2. Standardization of hot and cold channels (the rack forms several module groups, each group of modules intermediate hot channel, external cold channel, hot and cold channel isolation)
3. Standardization of cooling system (natural cooling - water evaporative cooling, standardized configuration of water circulation system)
4. Standardization of electrical system (modulation of electrical system, each module is independent of each other to ensure a stable and reliable system.)
5. Two-story building standardization (building shape, layout, protection, structural standardization)
20 transformer solutions - standard first-floor plan
20 transformer solutions - standard floor second-floor plan
Note: the information provided on the website may be used as general reference only. Please read our disclaimer here.
Article is closed for comments.